What people are saying - Write a review
We haven't found any reviews in the usual places.
Other editions - View all
according aqueduct attached average bands base bell bolts bottom bronze built capacity cast iron pipes Catskill aqueduct caused cent chamber Class closed coating concrete conduit connected consists constructed covered curve designed diameter disc discharge distance engineer experiments feet fire flow formula four gals gate given gives head holes hydrant inch increased inlet inside joint kind laid latter lead leakage length less loss lower machine Manufactured masonry means measuring metal meter miles obtained occur operating outlet passing pipe-line piston placed plates practically pressure prevent protection pumping quantity record reservoir resistance ring River riveted shows side space square stand-pipe standard steel strength supply surface TABLE tank thickness tube tunnel turned upper usually valve vertical wall weight York
Page 629 - The inspector representing the purchaser shall have free entry, at all times while work on the contract of the purchaser is being performed, to all parts of the manufacturer's works which concern the manufacture of the material ordered. The manufacturer shall afford the inspector, free of cost, all reasonable facilities to satisfy him that the material is being furnished in accordance with these specifications. All tests...
Page 629 - Material which, subsequent to the above tests at the mills, and its acceptance there, develops weak spots, brittleness, cracks or other imperfections, or is found to have injurious defects, will be rejected at the shop and shall be replaced by the manufacturer at his own cost.
Page 626 - ... in. in thickness, around a pin the diameter of which is equal to twice the thickness of the specimen.
Page 631 - The manufacturer shall afford the inspector, free of cost, all reasonable facilities to satisfy him that the material is being furnished in accordance with these specifications. All tests and inspection shall be made at the place of manufacture prior to shipment, and shall be so conducted as not to interfere unnecessarily with the operation of the works.
Page 619 - Specimen bars of the metal used, each being 26 inches long by 2 inches wide and 1 inch thick, shall be made without charge as often as the engineer may direct, and, in default of definite instructions, the contractor shall make and test at least one bar from each heat or run of metal. The bars, when placed flatwise upon supports 24 inches apart and loaded in the center, shall...
Page 583 - To this material sufficient oil shall be added to make a smooth coating, tough and tenacious when cold, and not brittle nor with any tendency to scale off. Each casting shall be heated to a temperature of 300...
Page 584 - The contractor shall provide all tools, testing machines, materials and men necessary for the required testing, inspection and weighing at the foundry of the pipes and special castings; and, should the purchaser have no inspector at the works, the contractor shall, if required by the engineer, furnish a sworn statement that all of the tests have been made as specified, this statement to contain the results of the tests upon the test bars.
Page 629 - Chemical Composition. — 3. The steel shall conform to the following; requirements as to chemical composition : Ladle Analyses.
Page 584 - The engineer shall be at liberty at all times to inspect the material at the foundry, and the molding, casting and coating of the pipes and special castings. The forms, sizes, uniformity and...